On February 4, 2015, the Regional Boiler/Gas Inspector of the Government of the Northwest Territories (GNWT) conducted an annual inspection of pressure vessels at a mine process plant. The inspection revealed signs of corrosion between metal identification tags and the pressure vessel walls on a number of air receivers.
Further testing confirmed that the pressure vessel’s walls were thinner in localized areas on three of the air receivers. To minimize the risk of a rupture, the Inspector requested that the air supply system be shut down. A 30 metre personnel exclusion zone was created to keep workers out of the area during repair.
Please be aware the current wildfire situation may cause unexpected connectivity issues which can impact our service to you on short notice.